section 5 - installation instructions
DETERMINING THE FLUE LENGTH
5.9 CUTTING HORIZONTAL FLUE TERMINAL RSF303 (600MM LONG)
Mark cut length =
A or B + 47mm from terminal lip
required cut length (A or B + 47mm) around the circumference of the
2. Dress the cut end to make sure all burr’s are removed and the cut
edge is in its original shape.
3. Mark the inner tube 10mm longer than the outer tube around its
circumference and cut following the mark to ensure its cut square.
4. Remove all burrs and place a light chamfer on the outer edge to aid
Centre of turret to edge of turret = 100mm
Turret has a ue insertion of 30mm
The white outer ue tube must protrude the wall by 17mm.
From centreline of turret to wall. Rear mount 155mm, side (including clearance) 200mm
Flue length measured from outer terminal lip
to end of outer ue
A or B + 47mm
Minimum clearance 2.5mm
wall dimension A + 47mm.
Note. Minimum dimension A which can be accommodated is
wall dimension B + 47mm.
Note. Minimum dimension B which can be accommodated is
136mm (with minimum clearance of 2.5mm).